Solar Water Heating System Maintenance and Repair
Solar energy systems require periodic inspections and routine maintenance to keep them operating efficiently. Also, from time to time, components may need repair or replacement. Call Freier's Electric and Heating, Inc. for details on Planned Maintenance Agreements that are available to you at 715-273-3658.
You might be able to handle some of the inspections and maintenance tasks on your own, but others may require a qualified technician like Freier's Electric and Heating, Inc.
For some older systems, it may be more cost effective to replace, shut off, or remove the solar system than to have it repaired. Freier's Electric and Heating, Inc can help you with this decision as well.
Periodic Inspection List
Here are some suggested inspections of solar system components. Also read your owner's manual for a suggested maintenance schedule.
Visually check for shading of the collectors during the day (mid-morning, noon, and mid-afternoon) on an annual basis. Shading can greatly affect the performance of solar collectors. Vegetation growth over time or new construction on your house or your neighbor's property may produce shading that wasn't there when the collectors were installed.
Dusty or soiled collectors will perform poorly. Periodic cleaning may be necessary in dry, dusty climates.
Collector glazing and seals
Look for cracks in the collector glazing, and check to see if seals are in good condition. Plastic glazing, if excessively yellowed, may need to be replaced.
Plumbing, ductwork, and wiring connections
Look for fluid leaks at pipe connections. Check duct connections and seals. Ducts should be sealed with a mastic compound. All wiring connections should be tight.
Piping, duct, and wiring insulation
Look for damage or degradation of insulation covering pipes, ducts, and wiring.
Flashing and sealant around roof penetrations should be in good condition.
Check all nuts and bolts attaching the collectors to any support structures for tightness.
Pressure relief valve (on liquid solar heating collectors)
Make sure the valve is not stuck open or closed.
Dampers (in solar air heating systems)
If possible, make sure the dampers open and close properly.
Pumps or blowers
Verify that distribution pumps or blowers (fans) are operating. Listen to see if they come on when the sun is shining on the collectors after mid-morning. If you can't hear a pump or blower operating, then either the controller has malfunctioned or the pump or blower has.
Heat transfer fluids
Antifreeze solutions in liquid (hydronic) solar heating collectors need to be replaced periodically. It's a task best left to a qualified technician. If water with a high mineral content (i.e., hard water) is circulated in the collectors, mineral buildup in the piping may need to be removed by adding a de-scaling or mild acidic solution to the water every few years.
Check storage tanks, etc., for cracks, leaks, rust, or other signs of corrosion.
For more information about solar water heating systems, see the following: